The Ontario Building Code | Ball Tests
22.214.171.124. Ball Tests
(1) Where a ball test is made, a hard ball dense enough not to float shall be rolled through the pipe.
(2) The diameter of the ball shall be not less than 50 mm where the size of the pipe is 4 in. or more.
7.3.7. Testing of Potable water Systems