The Ontario Building Code | Application
(2) The total daily design flow for a Class 2 sewage system shall be calculated based on the fixturesdischarging to the system as follows:
(a) 200 L per fixture unit where there is a supply of pressurized water, and
(b) 125 L per fixture unit where there is no supply of pressurized water.
8.4.2. design and Construction Requirements