The Ontario Building Code | Construction Requirements
188.8.131.52. Construction Requirements
(1) The treatment unit used in conjunction with a leaching bed constructed as a shallow buried trench shall provide an effluent quality that does not exceed the maximum concentrations set out opposite a Level IV treatment unitin columns 2 and 3 of Table 184.108.40.206.
(2) The effluent shall be distributed through a pressurized distribution system having a pressure head of not less than 600 mm when measured to the most distant point from the pump.
(3) The pump chamber shall be sized to provide sufficient storage volume so that the effluent is evenly dosed on an hourly basis over a 24-hour period.
(4) A shallow buried trench shall not be constructed unless the soil orleaching bed fill is sufficiently dry to resist compaction and smearing during excavation.
(5) Every chamber shall be as wide as the shallow buried trench in which it is contained, and the cross-sectional height of the chamber at its centre point shall not be less than half the width of the trench.
Note: On January 1, 2018, Sentence 220.127.116.11.(5) of Division B of the Regulation is amended by striking out "chamber" and substituting "chamberor leaching chamber". (See: O. Reg. 139/17, s. 66)
(6) Every chamber shall contain only one pressurized distribution pipe.
Note: On January 1, 2018, Sentence 18.104.22.168.(6) of Division B of the Regulation is amended by striking out "chamber" and substituting "chamberor leaching chamber". (See: O. Reg. 139/17, s. 66)
8.7.7. Type A Dispersal Beds