The Ontario Building Code | Incinerators
(1) service rooms containing incinerators shall be separated from the remainder of the building by a fire separation having a fire-resistance rating of not less than 2 h.
(2) The design, construction, installation and alteration of each indoor incinerator shall conform to nfpa 82, "Incinerators, Waste and Linen Handling Systems and Equipment".
(3) Every incinerator shall be connected to a chimney flueconforming to the requirements in Section 9.21. and serving no other appliance.
(4) An incinerator shall not be located in a room with other fuel-fired appliances.