22.214.171.124. walls in Exits
(1) Except as provided in Sentence (2), at least 90% of the exposed surfaces of every wall in an exit shall have a surface flame-spread rating of not more than 25.
(2) At least 75% of the wall surface of a lobby used as an exitin Article 126.96.36.199. shall have a surface flame-spread rating of not more than 25.
This material is COPYRIGHT © QUEEN'S PRINTER FOR ONTARIO, 2008-2018
This site is not an offical copy or maintitned by the Government of Ontario.