The Ontario Building Code | Hose Stations
18.104.22.168. Hose Stations
(1) Everybuilding in a camp for housing of workers providing sleeping accommodation for more than 30 persons shall be provided with a hose station that is protected from freezing and equipped with a hose of sufficient length so that every portion of the building is within the range of a hose stream.
(2) Hose stations required in Sentence (1) shall be located near an exit.
(3) Hoses referred to in Sentence (1) shall be not less than 19 mm inside diam and shall be connected to a central water supply or to a storage tank having a capacity of at least 4 500 L with a pumping system capable of supplying a flow of at least 5 L/s at a gauge pressure of 300 kPa.
9.10.22. Fire Protection for Gas, Propane and Electric Cooktops