The Ontario Building Code | Silencing of Alarm Signals
126.96.36.199. Silencing of Alarm Signals
(1) Except as permitted by Sentence (3), a fire alarm system shall be designed so that when an alarm signal is actuated it cannot be silenced automatically before a period of time has elapsed that is not less than,
(a) 5 min for a buildingnot required to be equipped with an annunciator, and
(b) 20 min for any other building.
(2) Except as permitted by Sentences 188.8.131.52.(9) and 184.108.40.206.(3) and (4), a fire alarm system shall not incorporate manual silencing switches other than those installed inside the fire alarm control unit.
(3) Except as provided by Clause 220.127.116.11.(4)(a), in a care and treatment occupancy an alert signal is permitted to be silenced automatically after 1 min.