The Ontario Building Code | Minimum Lighting Requirements
220.127.116.11. Minimum lighting="http://thehandyforce.com/electrical/" title ="East York Electrician">lighting Requirements
(1) An exit, a public corridor, a corridor providing access to exitfor the public, a corridor serving patients or residents in a Group B, Division 2 or 3 occupancy, a corridor serving classrooms, an electrical equipment room, a transformer vault and a hoistway pit shall be equipped to provide illumination to an average level not less than 50 lx at floor or tread level and at all points such as angles and intersections at changes of level where there are stairs or ramps.
(2) The minimum value of the illumination required by Sentence (1) shall not be less than 10 1x.
(3) Rooms and spaces used by the public shall be illuminated as described in Article 18.104.22.168.
(5) Elevator machine rooms shall be equipped to provide illumination to an average level of not less than 100 lx at floor level.
(6) Every place of assembly intended for the viewing of motion pictures or the performing arts, shall be equipped to provide an average level of illumination at floor level in the aisles of not less than 2 lx during the viewing.
(7) Every area where food is intended to be processed, prepared or manufactured and where equipment or utensils are intended to be cleaned shall be equipped to provide illumination to a level of not less than 500 lx measured at the floor level.
(8) Every storage room, dressing room, sanitary facility, service area and corridor serving the areas in Sentence (7) shall be equipped to provide illumination to a level of not less than 300 lx measured at the floor level.