The Ontario Building Code | Location of Exits
126.96.36.199. Location of Exits
(1) Except as permitted by Sentences (2), 188.8.131.52.(4) and 184.108.40.206.(13) to (16), if more than one exit is required from a floor area, the exits shall be located so that the travel distance to at least one exitshall be not more than,
(a) 25 m in a high hazard industrial occupancy,
(b) 40 m in a business and personal services occupancy,
(i) the public corridor is not less than 9 m wide,
(iii) the building is sprinklered, and
(iv) not more than one-half of the required egress doorway ="http://thehandyforce.com/doors/" title ="Toronto Door installer">doorways from a room or suiteopen into the public corridor if the room or suite is required to have more than one egress doorway ="http://thehandyforce.com/doors/" title ="Toronto Door installer">doorway,
(e) 60 m in any storage garage that conforms to the requirements of Article 220.127.116.11., and
(f) 30 m in any floor area other than those referred to in Clauses (a) to (e).
(2) Except for a high hazard industrial occupancy, Sentence (1) need not apply if exits are placed along the perimeter of the floor area and are not more than 60 m apart, measured along the perimeter, provided each main aisle in the floor area leads directly to an exit.
(3) Exits shall be located and arranged so that they are clearly visible or their locations are clearly indicated and they are accessible at all times.