The Ontario Building Code | Urinals
(2) A urinal described in Sentence (1) shall have,
(a) no step in front,
(i) is not less than 300 mm long,
(ii) has its centre line 1 000 mm above the finished floor,
(iii) is located not less than 380 mm and not more than 450 mm measured horizontally from the vertical centre line of the urinal, and
(iv) complies with Sentence 184.108.40.206.(7), and
(c) a minimum depth of 345 mm measured from the outer face of the urinal rim to the back of the fixture.
(a) operable using a closed fist, and
(b) mounted no higher than 1 200 mm above the finished floor.
(4) Where privacy screens are installed for a urinal described in Sentence (1), they shall,
(a) be mounted a minimum of 460 mm from the centre line of the urinal, and
(b) have a clearance of at least 50 mm from the grab bars required by Clause (2)(b).