220.127.116.11. Tracer wire
(1) Except as provided in Sentence (2), a 14 gauge TW solid copper light coloured plastic coated tracer wire shall be attached to every non-metallic water service pipe or fire service main.
(2) Where a water service pipe or fire service main is detectable without the tracer wire referenced in Sentence (1), the tracer wire may be omitted.
This material is COPYRIGHT © QUEEN'S PRINTER FOR ONTARIO, 2008-2018
This site is not an offical copy or maintitned by the Government of Ontario.