The Ontario Building Code | Number of Required Exits
18.104.22.168. Number of Required Exits
(1) Except as provided in Sentences (2) and (3) and Subsection 9.9.9., at least two exits shall be provided from every floor area, spaced so that the travel distance to the nearest exit is not more than,
(a) 40 m in the case of business and personal services occupancies,
(b) 45 m for all occupancieswhere the floor area is sprinklered, and
(c) 30 m for all other occupancies.
(2) Except as provided in Subsection 9.9.9., a single exit is permitted from each storey in buildingsof 1 and 2 storeys in building height provided the floor area and travel distance requirements conform to those required in Article 22.214.171.124. and the total occupant load served by an exit facility does not exceed 60 persons.
(3) Inboarding, lodging or rooming houses,
(a) where sleeping accommodation is provided for not more than eight persons, a single exitis permitted from each floor area, or
(b) where sleeping accommodation is not provided in the basement, a single exit is permitted from the basementfloor area.