The Ontario Building Code | Portions of Buildings Considered as Separate Buildings
126.96.36.199. Portions of buildings Considered as Separate Buildings
(1) Except as provided in Sentence (2), where a vertical fire separation having a fire-resistance ratingof at least 1 h separates a portion of a building from the remainder of the building and there are no openings through the fire separation other than those for piping, tubing, wiring and conduit, the requirements for fire alarm and detection systems is permitted to be applied to each portion so separated as if it were a separate building.
(2) The permission in Sentence (1) to consider separated portions of a building as separate buildingsdoes not apply to service rooms and storage rooms.