The Ontario Building Code | Sprinklers in Lieu of Fire Detectors
184.108.40.206. Sprinklers in Lieu of Fire detectors
(1) Fire detectorsrequired by Article 220.127.116.11. and heat detectorsrequired by Sentence 18.104.22.168.(2) need not be provided within a floor area if the floor areais sprinklered and the sprinkler system is electrically supervised in conformance with Sentence 22.214.171.124.(3).