The Ontario Building Code | Installation and Conformance to Standards
18.104.22.168. installation and Conformance to Standards
(1) The carbon monoxide alarms required by Article 22.214.171.124. shall,
(a) except as permitted in Sentence (2), be permanently connected to an electrical circuit and shall have no disconnect switch between the overcurrent device and the carbon monoxide alarm,
(b) be wireref ="http://thehandyforce.com/electrical/" title ="Electricians in East York">wired so that its activation will activate all carbon monoxide alarms within the suite, where located within a suite of residential occupancy,
(d) conform to,
(i) CAN/CSA-6.19, "residential Carbon Monoxide Alarming Devices", or
(ii) UL 2034, "Single and Multiple Station Carbon Monoxide Alarms".
(2) Where the building is not supplied with electrical power, carbon monoxide alarms are permitted to be battery operated.
6.2.13. ventilation for Laboratories