The Ontario Building Code | Cleanout Fittings
126.96.36.199. Cleanout Fittings
(1) Every plug, cap, nut or bolt that is intended to be removable from a ferrous fitting shall be of a non-ferrous material.
(2) A cleanout fitting that as a result of normal maintenance operations cannot withstand the physical stresses of removal and reinstallation or cannot ensure a gas-tight seal shall not be installed.
(3) A screw cap or test cap shall not be used as a cleanoutplug or cover.