The Ontario Building Code | Saddle Hubs
18.104.22.168. Saddle Hubs
(1) Except as provided in Sentence (2), a saddle hub or fitting shall not be installed in drainage systems, venting ="http://thehandyforce.com/interior/bathroom-renovations/" title ="Toronto Bathroom renovation inspiration">venting systems or water systems.
(2) A saddle hub or saddle clamp may be installed in a building drain or building sewerof nominal diameter not less than 8 in. and that is in service provided that the connecting branch is at least two pipe sizes smaller than the run of the building drain or building sewer to which it is connected.