The Ontario Building Code | Group C, up to 6 Storeys, Sprinklered, Noncombustible Construction
220.127.116.11. Group C, up to 6 Storeys, Sprinklered, Noncombustible Construction
(1) A building classified as Group C is permitted to conform to Sentence (2) provided,
Note: On July 1, 2017, Sentence 18.104.22.168.(1) of Division B of the Regulation is amended by adding "other than a retirement home" after "Group C" in the portion before Clause (a). (See: O. Reg. 139/17, s. 18)
(a) except as permitted by Sentence 22.214.171.124.(1), the building is sprinklered,
(b) it is not more than 6 storeys in building height, and
(c) it has a building area,
(i) that is not limited if the building is not more than 2 storeys in building height,
(ii) not more than 12 000 m2 if 3 storeys in building height,
(iii) not more than 9 000 m2 if 4 storeys in building height,
(iv) not more than 7 200 m2 if 5 storeysin building height, or
(v) not more than 6 000 m2 if 6 storeysin building height.
(2) Except as permitted by Article 126.96.36.199., the buildingreferred to in Sentence (1) shall be of noncombustible construction, and,
(a) except as permitted by Sentence (3), floor assemblies shall be fire separationswith a fire-resistance rating not less than 1 h,
(b) mezzaninesshall have a fire-resistance rating not less than 1 h, and
(c) loadbearingwalls, columns and arches shall have a fire-resistance rating not less than that required for the supported assembly.
(3) In a building that contains dwelling units that have more than 1 storey, subject to the requirements of Sentence 188.8.131.52.(3), the floor assemblies, including floors over basements, which are entirely contained within these dwelling units, shall have a fire-resistance rating not less than 1 h but need not be constructed as fire separations.